Comment on page
This example Data Stream demonstrates how to use this Listener to retrieve SD5500 X02's pressure and temperature values from the ifm Server.
Drag the ifm Listener onto the canvas and rename it. Link the output endpoint to the printer and save the Data Stream.
Select the Agent and click Configure. In this case, keep the default Collection and polling interval.
Enter the Connection details for ifm moneo: server url, endpoint, and security.
In this case, select the server url, "opc.tcp - SignAndEncrypt - Basic256Sha256 - Binary" as the endpoint and tick Auto Accept Server Certificate.
In this case, set security to UserName and then enter credentials for the username and password.
Define the tags input. In this case, keep the default (Using Drilldown).
Set the branch levels. In this case, we'll select 4 levels: Objects -> Devices -> AL1352 192.168.0.110:80 -> SD5500 X02.
Select from the Available Tags and click Add Selected Tags to populate the Tags Grid. In this case, select Pressure and Temperature.
Enter the Alias and Type for the tags in the Tags Grid. In this case, enter their tag names as the alias and set their type to String.
Apply the changes, save the Data Stream, and publish it.
Let's look at the Live Data View. Observe that the current values of SD5500 X02's pressure and temperature nodes are printed every 10 seconds.